PREVENTIVE MAINTENANCE CHECKS AND SERVICES (PMCS)
Determining (PMCS) Intervals.
Organizational PMCS on the AGPU should
a. To ensure that the AGPU is ready
be- performed on a weekly (W) basis,
for operation at all times, it must be
monthly (M) basis, semi annual (S)
inspected systematically so defects may
basis, and per-hour-of-operation
be discovered and corrected before they
result in serious damage or failure.
running time meter on the GTE is used to
The necessary preventive maintenance
determine AGPU operating time.
checks and services that are to be per-
formed by Organizational personnel are
d. PMCS for Units in Continuous
Operation. For PMCS performed on an
operating time basis, perform PMCS as
b. Defects discovered during opera-
close as possible to the time intervals
For units in continuous op-
tion will be noted for future correc-
Stop operation immediately If a
eration, perform PMCS before starting
deficiency is noted which would damage
operation if continuous operation will
All deficiencies and
extend service past that which is shown.
short-comings will be recorded together
e. (A, N, MC) Preventive Mainte-
with the corrective action taken on the
applicable form. Air Force users shall
refer to the applicable Inspection manu-
contains a tabulated listing of PMCS
which shall be performed by Organiza-
als and work card sets in the TO 35C2-3
The item numbers are
Marine Corps users should re-
listed consecutively and Indicate the
sequence of minimum requirements.
fer to current issue of TM 11275-15/1.
Organizational Preventive Maintenance Checks and Services
Total M/H: 0.3
Weekly (40 Hrs)
Total M/H: 1.6
Monthly (100 Hrs)
Total M/H: 2.6
Semi Annual (500 Hrs)
CONTROL PANEL AND ELECTRICAL COMPARTMENT
(1) Lower control panel for maintenance (para-
graph 4-24) and inspect control panel wiring
harness for loose wiring connections and
damaged or burned wires.
(2) Inspect components mounted on bulkhead
behind control panel:
(a) Inspect AC and DC main cantactors for
damage or loose connections.