ARMY TM 5-6115-633-14&P
Figure 42. Installing Power Plant.
Do not operate generator sets until power plant is properly grounded
from operating an ungrounded power plant.
To avoid damage to equipment, make certain of voltage, frequency, and
phase requirements of load being connected to generator sets.
(6) Refer to data plate on load terminal board cover and toTM 5-6115-585-12. Connect power plant to
system or equipment to be powered.
b. Grounding. Check that generator sets are grounded
to GROUND TERMINAL stud
on trailer body. Using
ground wire supplied, connect power plant to a suitable ground as described below. The following sources of a good
ground are listed in order of preference.
As a substitute for the supplied ground wire, any copper wire of at least
No. 6 AWG may be used.