ARMY TM 5-6115-633-14&P
Table 4-1. Unit Preventive Maintenance Checks and Services (PMCS). CONT.
H Hours of operation
M - Monthlv
Item to be
Before performing any maintenance
that requires climbing on or under
trailer, set trailer handbrakes, chock
wheels, and lower rear leg prop.
Injury to personnel could result from
trailer suddenly rolling or tipping.
Generator set checks and services in
this table are described as performed
on a single generator set. These
procedures must be performed on
that make up the AN/MJQ-18.
leaks, loose or missing components and
hardware, and unusual wear or
Fuel system must be above freezing
temperature when draining water and
sediment from strainer, filters,
Fuel Strainer and
Open drains on fuel strainer, and primary
and secondary filters. Drain water and
sediment (para 3-20, TM 5-6115-585-12).
Allow to drain until fuel runs clean.
Open drain on fuel tank and drain water
and sediment (para 3-13, TM 5-6115-
584-12). Allow to drain until fuels runs
Change 1 4 - 9